EMERGENCY OPERATION OF TYPE - AQ AALBORG BOILER
This presentation is intended to provide the step-by-step guidance to the emergency operation of the AQ type Aalborg boiler. It will show the user the proper sequence of actions. Generally speaking, following is to be done: change over key for Boiler Mode from Auto to Manual, change Burner to manual by pressing Burner Auto button (green light will go off), change Combustion Air Fan selector switch from Auto to 0 position and confirm that the vanes are fully shut and then change to Manual potirion (the fan starts running), press button Combustion Controller Off to put off the controller. There are two potentiometers on the Panel for controlling the Air flow and the Oil flow when the Boiler is fired in Emergency mode. The Air flow and Oil flow Indicators continue to show the actual air and oil flow...
The "Read Later" function allows you to add material to this block with just one click. Just click on the icon and read the articles that interest you at any convenient time.